The main sources of air pollution are not people, but new building decoration materials, cleaners, adhesives, modern office supplies and so on. Therefore, the use of low pollution value of green environmental protection data can make the pharmaceutical factory clean room pollution status is very low, which is also a good way to reduce fresh air load and energy consumption.
In the design of clean rooms for energy-saving design in pharmaceutical dust-free workshop, the standard of air cleanliness grade should be determined. On the premise of guaranteeing the quality of consumption, the factors such as process consumption ability, equipment size, operation mode and the connection mode of consumption process before and after, the number of operators, equipment automation level, equipment maintenance space and equipment cleaning mode should be considered comprehensively. In order to reduce investment and operation costs, to reach the energy-saving request.
For high illumination operation points, partial illumination can be used, but the minimum illumination standard of the whole workshop should not be improved. At the same time, non-consumer room lighting should be lower than consumer room, but not less than 100 lumens is appropriate. According to the illumination level of Japanese industrial standard, the medium-precision operation is set at 200 lumens, while the pharmaceutical factory operation will not exceed the medium-precision operation. Therefore, it is appropriate to reduce the minimum illumination from 300 lumens to 150 lumens. This measure can significantly save energy.
On the premise of ensuring clean effect, reducing the number of ventilation and air supply is one of the important means of energy saving. The number of ventilation is closely related to consumption technology, advanced level of equipment and layout, size and shape of clean room, and personnel density. If there is a room equipped with ordinary ampoule filling machine, it needs a higher number of ventilation, while the water needle consumption room with air purification and installation of washing and filling combined motor can adhere to the same cleanliness only by a lower number of ventilation.
More information can be consulted by clicking on our website: http://www.hnsfk.com.